The GE Hydran Ti is a small on-line early warning transmitter. It is permanently mounted on the transformer and will provide personnel with a single reading. The Hydran Ti is a small and easy to setup continuous DGA monitor. It provides the basic information used by IEEE® Standard C and can be used as. GE Hydran Ti | Single Gas Transformer DGA. Basic transformer monitoring device comprised of a fault gas sensor (Ti) and a separate controller (Ci) .
|Published (Last):||3 March 2015|
|PDF File Size:||6.33 Mb|
|ePub File Size:||8.55 Mb|
|Price:||Free* [*Free Regsitration Required]|
Email to friends Share on Facebook – opens in a new window or tab Share on Twitter – opens in a new window or tab Share on Pinterest – opens in a new window or tab. Much better than relying on manual oil sampling. Suwanee, Georgia, United States.
Installation Guide Hydran i System_图文_百度文库
The Hydran Ti is a small on-line early warning transmitter. After the HTi has performed the first-time power-up sequence and then the self-test sequence, verify it displays the following messages at the rate of one every five seconds: The item may be a factory second or a new, unused item with defects.
Remove only the two screws used to fasten the CPU module and identified with arrows see Figure on page We would ask that potential buyers please view the photographs carefully.
The item may be missing the original packaging, or in the original packaging but not sealed. Any failure which is the basis for a warranty claim shall not be cause for extension of the duration of the applicable Warranty Period. Reproduction, in whole or in part, to create working hardware or software for other than General Electric Canada products is strictly prohibited, except as permitted by written license agreement with General Electric Canada.
Upon receiving such notice, General Electric Canada may lend telephone support or patches.
Product Detail – GE Hydran Ti | Single Gas Transformer DGA | GAE
Paint, liquid Teflon, vehicle exhaust, spray can, black pitch, thinner, RTV Room Temperature Vulcanization; silicon-based mastic and solvent. We have ratings, but no written reviews for this, yet. We cannot negotiate price or terms after the auction has closed.
Always wrap the tape counter to the threads see Figure on page Otherwise, armored cables can be used. Drill, bits and fasteners for mounting the Hydran Ci Controller? See the comments on location 2. See all condition definitions – opens in a new window or tab. Laredo, Texas, United States. One Hydran TW tube wrench per site is recommended.
If Products covered by this manual do not meet the above warranties during the applicable Warranty Period, the Buyer shall promptly notify General Electric 21ti in writing but not 2201ti than 30 days and make the Products available promptly for correction.
Learn More – opens in a new window or tab Any hydram shipping is paid in part to Pitney Bowes Inc. Drain valve bottom of tank: Jede Abweichung davon k?
For a typical transformer, the four most common locations to install the HTi are shown in Figure on page Report item – opens in a new window or tab. If additional openings must be made, apply a protective coating to the gydran metal around the hole to prevent rust.
Refer to eBay Return policy for more details. This item will ship to United Statesbut the seller has not specified shipping options. Skip to main content. Any included or attached hardware schematics and technical descriptions, or software listings that disclose source code, are for information purposes only.
Hydran 201Ti Transformer Monitoring System
Add to hydarn list Remove from watch list. Add to watch list Remove from watch list. Please enter a valid ZIP Code. The two alarm indicators of the door-mounted push-buttons are off. This indicates the sensor is being heated. IBM System x M2 wi Modbus or Hydran protocols available.
Fasten the module with the two screws see Figure on page Bucket and oil-absorbing rags? Subject to credit approval. Full system self test and self-diagnostics.
If any functional deficiencies are discovered and are reported to General Electric Canada within the Warranty Period, General Electric Canada agrees to use due diligence to correct such deficiencies within 30 days after receipt of such notification. This item may or may not be in the original packaging. Figure – Do Not Touch the Membrane.
Use only Teflon tape to seal the threads of both the adaptor and Hydran sensor.
Mouse over to Zoom – Click to enlarge. Never apply high voltages to the components of a Hydran i System, even if they are equipped with surge protection devices that could be damaged by Megger tests. Minimum monthly payments are required.